- 01 Hotline : (+84) 0965 929 114 – Email: [email protected]
- 02 Hotline : (+84) 0962 683 555 – Mr Tuan Anh
- Phone : (+84) 046253.8882 / Fax : (+84) 046253.8882
* Advantages when using the services of E & C Pacific Unbeatable price ( the cheapest in Hanoi ) Construction of the time required Best finishing quality
Maintenance process – checking system
A. INSPECTION SYSTEM FIGHTING
1. Check the fire pump control panel :
– Check light phase : To Test view 3
-phase power to have lost phase .
– Overload indicator : To Test see pump overheating or overload .
– Check the Volt , Ampere : View input voltage value is not sufficient .
– Check the operation mode of the cabinet ( always in Auto mode ) .
– Check the overall CB , CB pump controller : See CB unusual incidents not , CB is in state of ON .
– Intermediate relay , delay timer : Test to see the good points shutdowns .
2. Check the fire pump:
– Electric pumps, compensation pump: There is not overheating, the rotation speed is normal, not strange cries, check if the machine has no electric leakage.
– Diesel Pumps:
+ There is not overheating, the rotation speed is normal, not strange cries, check if the machine has no electric leakage.
+ Check the status of the oil leak.
+ Check the average offer Volt average, average water level, the exposed pile, the average leakage.
– Check the fire main pipe on the floor:
+ Check the valve main water pipeline for the floor level.
+ Check the main water supply pipe for the floor have not been leaked.
+ Check the water pressure gauges.
+ Check the system of fire sprinklers in the floors.
3. Maintenance, cleaning and maintenance Fire extinguisher box fire
– Hygiene Fire box and fire extinguisher in the room with a cloth wipe and alcohol.
– Check the pressure of the extinguisher.